Sanlian/Kubota Brand S Type Split Casing Pump
|FOB Price:||US $5,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $5,000/ Piece|
|Production Capacity:||50000 Pieces Per Year|
|Transport Package:||Plywood Cases|
|Payment Terms:||L/C, T/T, D/P|
- Model NO.: S type
- Working Pressure: Low Pressure Pump
- Position of Pump Shaft: Horizontal Pump
- Mounting Height: Since Irrigation Centrifugal Pumps
- Usage: Pump
- Head: 10-125m
- Specification: CE; ISO9001
- HS Code: 8413709990
- Impeller Number: Single-Stage Pump
- Influent Type of Impeller: Double-Suction Pump
- Pump Casing Combined: Horizontal Split Pumps
- Impeller: Closed
- Capacity: 133-3170m3/H
- Trademark: Sanlian/Kubota
- Origin: Anhui, Ma′anshan
Speed: 2900r/min, 1450r/min970r/min
Matched power: 18.5-850kW
S type pump is single stage double suction horizontal centrally-split centrifugal pump which can transport clean water and the liquids with physical and chemical properties similar to clean water, and the temperature of liquid can not exceed 80º C.
It is applicable to water supply and drainage in factory, mine, city, power station, agriculture irrigation and all kinds of hydraulic engineering.
Both inlet and outlet of S type pump are below the pump's axial central line. They are perpendicular with axial line and horizontally placed in the middle of pump casing. There is no need to remove inlet, discharge pipeline and electric motor(or some other motors). The pump rotates clockwise from the direction of the drive end. The pump which rotates anticlockwise can also be manufactured according to the requirements, but it should be specified when ordering.
S type pump is mainly made up of pump casing, pump cover, impeller, shaft and double suction seal ring, shaft sleeve and bearing, etc. Except that the material for the bearing is first grade carbon steel, the remained are all made of cast steel(See the structural drawing of pump). Other material can also be made according to client's requirements.
Pump casing and pump cover compose an impeller's working room. The installation vacuum gauge and pipeline bolt hole on the pressure gauge are designed for the inlet and outlet flange. After the static balance test on the impeller, it is fixed with the shaft sleeve and sleeve nuts on both sides. The axial location can be adjusted through the sleeve nut. The impeller's axial force makes use of the symmetric layout of its vane to keep in balance. The rest little residual axial force is borne by the bearing at the shaft end.